I’m dying here.
35 hours deep in 2 days and I can not solve this.
I have existing 4WB smokes and a new MS9050UD and MMF-301’s
For each smoke and pulls. Also an altronix AL300ULXB on site.
Can anyone lend me brain power to help reset the power of these smoke detectors please?
Search found 2 matches
Search found 2 matches • Page 1 of 1
- Mon Feb 05, 2018 10:01 pm
- Forum: Fire Alarm Help
- Topic: Question regarding my System Sensor 4W-B
- Replies: 14
- Views: 2640
Ok ladies and gents, I need help badly. I charter school with no money asked for help after their FACP caught fire. It was an NX8CF panel now is a 9050UD With 4 wire smokes. I’m putting MMF-301’s at every existing smoke and pull station until the raise enough money to do a complete upgrade to fully ...