FireFinder XLS and Cerberus Pro Modular are 100% identical except for the yellow color scheme. The name change was made in 2016, so if the mall was just upgraded, the new system is a Cerberus Pro Modular. Migration kits are available to install Cerberus Pro Modular equipment into an existing MXL cabinet.El Chupacabra wrote: ↑Sun Oct 11, 2020 12:22 pmThis leads me to believe that the new system is a FireFinder XLSV/Cerberus PRO Modular. The pull stations and speakers in the original part of the mall remain untouched; I wonder if they will be upgraded in the near future.
I'm particularly surprised that the conventional initiating devices were not upgraded in 2016
As for the old pull stations, they have probably had XTRI-S or HTRI-S addressable modules installed. (and before that, TRI-B6's.) If they're mounted at compliant heights and meet code requirements, the pulls don't need to be replaced.
Are the replaced pulls in the new part HMS-series (which looks identical to the MSI-series that works with the MXL, and uses an Allen key to reset) or the all-new XMS series (which uses a T45 key to reset)?