Your Advance, if a 2-wire model, should have an option to select between continuous and temporal. If 4-wire, the horn is coded by the power source.Gentex Guy wrote: ↑Fri Dec 11, 2020 11:28 pmYeah I did mention that the Exceder sounds immediately when set on continuous, the Advance does not. I have the strobe on 15cd, and I did see when selecting the candela that it can only do 15cd on 12 volts, but I never set it higher anyways. Also, I have the positive and negative on the panel go directly to the positive and negative of the alarm. I don't have any other devices or an end of line resistor since I'm just using it as a demo system.
How many devices are you hooking up at once?
I'm a bit concerned - the list you provided me here...
has 24 VDC devices - specifically the EST Integrity/Genesis devices and possibly the AS if it's not the 12 volt version. I hate to ask so many questions, but it doesn't add up to me. Could you clarify your setup for me please?